SWIMMING POOL PUMP SUPPLIERS IN DUBAI & POOL PUMP INSTALLATION METHOD
We Infinite Leisure is the Swimming Pool Pump Suppliers in Dubai provides the best pool pumps and below are the top brands in the UAE’s market.
KRIPSL PUMP DETAILS:
KRIPSL PUMP SPARE PARTS DETAILS:
METHOD FOR SWIMMING POOL PUMP INSTALLATION.
INSTALLATION AND ASSEMBLY WORK WARNINGS
The methodology of installing kripsol swimming pool pump suppliers in Dubai shall be same all the pump rooms. The referred astral swimming pool pumps are the centrifugal type and are to be used for the circulation of water through the filter. For the sake of simplicity and identification on site, these shall be tagged based on their capacity and the area location. On shop drawings and checklist (covered under method statement of testing and commissioning) these shall be referred to as filtration / Circulation/ booster/nozzle pumps.
Once the level of the foundation is confirmed, the swimming pool pump foot bearing as to be measured and marked with suitable marker or chalk. The point of the fastener has to be drilled with a suitable approved drill bit. Pool pumps come self-aligned with the motor and strainer that are ready to be installed. These are assembled in the factory itself.
The drill bit points are drilled through for anchor provision and suitably approved inserts are inserted into its place. The water feature pump is positioned with an anti-vibration pad into its place and bolted with suitable studs and bolts. There shall be no inertia base since pool pumps weigh less and transmit less vibration to the surface.
The fountain pump suction and discharge ports are then jointed with the respective piping work.
Here the pools pump network can only be connected with the approval of hydro testing of the piping network by Consultant.
The terminal box joint has to be used correctly, thus preventing water from entering the terminal box of the electric motor. similarly, check that the packing gland has been placed and pressed correctly inside the joint.
They must be fixed in a horizontal position. These swimming pool pumps are not self-priming and they should be installed below water level. The suction pipe should be as short as possible in order to reduce the suction time. The place where the swimming pump is installed should be dry and aired at all times.
Particular notice should be paid to ensure that under no circumstances water gets into the motor and the electric voltage parts.
Should the envisaged use be different from that mentioned, adaptations and supplementary technical regulations may be necessary.
Once the entire installation works as to be offered for inspection as per ITP and checklist.
Before starting the swimming pool pump for the very first time, confirm the calibration of the motor electric protection mechanisms and check that the protectors against electrical and mechanical contacts are correctly positioned and well fixed.
It is suggested not to use the swimming pool during that first check of the pumping equipment installation.
ASSEMBLY AND MAINTENANCE WORK WARNINGS
National installation regulations should be taken into account when assembling and installing the fountain pumps.
Extraordinary attention should be paid to ensure that under no circumstances water gets into the motor and the electric voltage parts.
Some contact, even accidental, with the machine’s moving parts, should be avoided while the machine is operating and/or before it completely stops.
Wait until the machine has completely stopped in order to carry out any work on it.
Previous to undertaking any electrical or mechanical maintenance makes sure that the machine has been disconnected from the supply network and starting-up mechanisms are blocked.
Previous to working on the machine it is advisable to follow the steps below:
- Cut the machine voltage.
- Block the starting-up mechanisms.
- Check that there is no voltage in the circuits, including the auxiliaries and supplementary services.
- Wait until the wheel has stopped completely.
The mentioned list should be considered indicative and not binding, since there may be specific safety rules within specific safety procedures.
The mechanical parts shall be firmly secured and the machine support screws are to be in good condition.
Right positioning and fixing and the condition of the leading-in wires and isolation components.
In case of irregularity with regard to machine or motor temperature rise, stop the machine immediately and proceed with its repair.
In case of irregularity with regard to vibration, stop the machine immediately and proceed with its repair.
GENERAL SAFETY REGULATIONS
The jacuzzi pump machines indicated in its respective Manual are specially designed for the pre-filtering and recirculation of water in swimming pools.
They are designed to work with clean water.
Current regulations have to be respected for accident prevention.
All modifications to the nozzle pump require prior authorization from the manufacturer. Original spare parts and accessories Authorized by the manufacturer ensure greater safety. The pool filter pump manufacturer is exempt from all liability regarding any damage caused by unauthorized spare parts or accessories.
When working on each machine or on the units linked to them, disconnect the unit from the power supply and the start-up devices, as the electrical parts of the pool sand filter pump are live during operation.
All assembly and maintenance work must be carried out by qualified and authorized personnel who have carefully read the installation and service instructions.
To guarantee safety when operating the machine, you must comply with that set out in the installation and service instructions.
In the event of defective operation or faults, contact your supplier or nearest representative.
Pipe Fittings (Solvent welded type)
Valves & Strainers
Anchors and Supports
The Swimming Pool Pumps have to be stored at dry locations
The protective casings for the flanges as well as the protective covers have to be retained during storage.
The swimming pools pump bearings and seals have to be protected from sand, grit or other foreign materials.
HANDLING OF SWIMMING POOL PUMPS
During handling, all packing materials around the swimming pool pump such as plastic tape have to be removed.
Smaller fountain pumps can be handled by a single person while in the case of bigger pumps a lift sling is set around the eye bolt and a rope sling has to be used for this operation.
Call us if you have an enquiry, We are swimming pool pump suppliers in Dubai.