Experience Year-Round Swimming Comfort with Innovative Pool Heating and Cooling Systems in Dubai
We Infinite Leisure is the Swimming Pool Heating Cooling Pump Suppliers in Dubai provides the best pool heat pumps and below are the top brands in the UAE’s market. We ILP supply and install Calorex Heat Pump & Astral Heat Pump.
- Astral Swimming Pool Heating Cooling Pump Suppliers in Dubai
- Calorex Swimming Pool Heating Cooling Pump Suppliers in Dubai
Calorex Heat and Cool Pump Model
Adequate clearance has to be provided to service panels on the unit, recommend clearance would be 500mm minimum.
Once the level of the foundation is confirmed, the heat pump foot bearing as to be measured and marked with a suitable marker or chalk. The point of the fastener has to be drilled with a suitable approved drill bit. swimming pool heating cooling pump comes fully assembled that are ready to be installed. These are assembled in the factory itself.
The drill bit points are drilled through for anchor provision and suitably approved inserts are inserted into its place. The swimming pool heating cooling pump is positioned with an anti-vibration pad into its place and bolted with suitable studs and bolts. There shall be no inertia base since pool heat pumps transmit very less vibration onto the surface. The compressor is pre-installed with vibration eliminator to the heat pump chassis.
The heat pump inlet and outlet ports are then plumbed with the respective piping work. Here the swimming pool heating cooling pump network can only be connected on approval of hydro testing of the piping network by Main Contractor or Consultant.
The swimming pool heating cooling Pump must be connected after the filter in the return pipe to the pool
Suitable couplings should be installed locally to swimming pool heating cooling pump.
Particular attention should be paid to ensure that under no circumstances water gets into the motor and the electric voltage parts. If the swimming pool heating cooling pump installed at the lower level than swimming pool water then isolation valves should be fitted.
Drain valve or plug should be fitted to lower pipe to facilitate drain.
The condensation from the evaporator fins drains away through holes in the base of the unit via 1 ½” domestic waste piping. In this case, it is necessary to ensure that the swimming pool heating cooling pump is placed on a level plinth so that the condensate can run away with adequate fall to waste. A U trap should be incorporated into the pipework.
Once the entire installation work is completed it has to be offered for inspection.
When the pipework installation is complete the swimming pool heating cooling pump should be switched on and the system tested for leaks. Also, check the filter gauge to see that there is not an excessive increase in back pressure. If every aspect is then working normally the water circulating system is ready to use.
Pool Water circuit to and from unit to be able of maintaining within specified limits the rate of flow required by heat pump as per manufacturer recommended flow rate.
ASSEMBLY AND MAINTENANCE WORK WARNINGS
National installation regulations should be taken into account when assembling and installing the swimming pool heating cooling pump suppliers in Dubai.
Special attention should be paid to ensure that under no circumstances water gets into the electric voltage parts.
Some contact, even accidental, with the machine’s moving parts, should be avoided while the machine is operating and/or before it completely stops.
Wait until the machine has completely stopped in order to carry out any work on it.
Before responsibility, some electrical or mechanical maintenance make sure that the machine has been disconnected from the supply network and starting-up mechanisms are blocked.
Before operational on the machine it is advisable to follow the steps below:
- Cut the machine voltage.
- Block the starting-up mechanisms.
- Check that there is no voltage in the circuits, including the auxiliaries and supplementary services.
The mentioned list should be considered analytic and not binding, since there may be specific safety rules within specific safety procedures.
The body of heat pump has to be properly grounded.
The mechanical parts shall be firmly secured and the machine support screws are to be in good condition.
The inlet valve should be properly positioned in order to maintain the Astral AHP heat pump flow rate
Correct positioning and fixing and the condition of the leading-in wires and isolation components.
In case of irregularity with regard to machine or motor temperature rise, stop the machine immediately and proceed with its repair.
In case of irregularity with regard to vibration, stop the machine immediately and proceed with its repair.